Where a plastic pipe penetration through a hole in a floor or wall requires fire protection use retrofit surface mounted fire collars. Retorfit fire collars are suitable for the fire rating of pipe penetrations through cored holes or the fire rating of plastic pipe penetrations in concrete floors and walls and fire rated plasterboard walls. Suitable for use in existing and new multi level buildings or where rework may be required to fire rate pipe penetrations .
Important : Consult technical data for tested applications before commencing use .
FEATURES & BENEFITS
Complies to AS1530.4 & AS4072.1.
Fire rated up to 240 minutes.
Rated and approved for use with PVC, HDPE, PPR and PE pipes in concrete floor and wall. Pipe types approved may vary depending on the tested application .
Fire tested for conduits with cables and small pvc pipe penetrations in Fire rated Plaster walls
Low profile design (40mm height) for normal space, tight space and close to ceiling or wall applications.
For pipe clusters with limited space between each pipe.
One piece galvanised steel body with fixed mounting brackets.
Choose from 2 body sizes that suit multiple pipe diameters and types:
- Small body for pipe sizes 40/50/65mm (nom). - Large body for pipe sizes 80/90/100mm (nom).
TRADES & APPLICATIONS
Conduit with cables
Before commencing Retrofit collar installation seal the gap to the correct depth/width between the pipe and edge of pipe hole on the underside of the concrete floor or from the front of the wall with fire rated Blazebrake sealant. Refer to sealant instructions for correct use.
1.Concrete floor installation . Unlock metal tab and open up body (dia. A & B). Place body around pipe and reconnect tab. Push body up till feet are flush against underside of concrete floor (dia. C). Use 4 x fire rated anchors to secure fire collar. Ramset™ AnkaScrew™ 5x30mm Hex. Part No. - AS05030H
2. Fire rated Plasterboard Wall installation . Retrofit fire collars must be fitted to both sides of the fire rated plaster wall .Unlock metal tab and open up body (dia. A & B). Place body around pvc pipe or 3x25mm and reconnect tab. Push body along till feet are flush against front of FR Plaster wall (dia.D). Use 4 x 10g x 38mm Bugle head Laminating screws with 6mm steel washers to screw fire collar to wall.
Internal wall applications : To prevent the passage of fire and smoke from one side of the wall to the other irrespective for the fire source Retrofit fire collars must be fitted to both sides of an internal concrete of FR plaster wall for correct Australian fire standards compliance .
Refer to technical section for full installation details and tested applications before commencing use.
TECHNICAL DATA & DOCUMENTS
important : consult technical data for tested applications and fire ratings before commencing use . For applications outside those teated refer to your fire consultant for compliance advice .